“SB” series heavy duty pump delivers high flow and energy efficiency ultra performance. It is suitable for commercial swimming pool. 2 inch suction and discharge port with transparent lid. Ring lock seal design to eliminate suction leaks and to maximize suction efficiency.
Features: Asynchronous, Two poles Class insulation: 130 IPX5 Waterproof standard Built-in thermal protection Overload protection Available in 50Hz or 60Hz with 220V/380V/110V Special design union compatible for both Imperial and Metric measurement standard S.S 316 Shaft S.S 316 Mechanical seal
READ MORE HERE: POOL EQUIPMENT
Pump Mount Must: Be solid Level Rigid Vibration Free. Allow for gate valves in suction and discharge piping. Have adequate floor drainage to prevent flooding. Be protected from excess moisture. All adequate access for servicing pump and piping. NOTICE: Pump suction and discharge connections have moulded in thread stops, DO NOT try to screw pipe in beyond these stops. Allow use of short, direct suction pipe. (To reduce friction losses & don’t install the pump at more than 3M geometricalheight from water level) NEVER run pump dry! Running pump dry may damage seals,causing leakage and flooding! Fill pump with water before starting motor. Before removing lid: STOP PUMP before proceeding. CLOSE GATE VALVES in suction and discharge pipes. RELEASE ALL PRESSURE from pump and piping system. NEVER tighten or loosen screws while pump is operation. Do not block pump suction! To do so with body may cause severe or fatal injury. Children using pool must ALWAYS have close adult Supervision! Priming Pump: Release all air from filter and piping system: see filter owner manual. In a flooded suction system (water source higher than pump), pump will prime itself when suction and discharge valves are opened. If pump is not in a flooded suction system, unscrew and remove trap cover; fill trap and pump with water. Clean and inspect Ring; re-install on trap cover. Replace trap cover on trap; turn clockwise to tighten cover. NOTICE: Tighten trap cover by hand only. Pump should prime now. Priming time will depend on vertical length of suction lift and horizontal length of suction piping.
ROUTINE MAINTENANCE The only routine maintenance needed is inspection/cleaning of trap basket. Debris or trash that collects in basket, will choke off water flow through the pump. Follow instructions below to clean trap: Stop pump, close gate valve in suction and discharge, and release all pressure from system before proceeding. Unscrew trap lid (turn counterclockwise). Remove strainer basket and clean. Be sure all holes in basket are clear,flush basket with water and replace in trap with large opening at pipe connection port (between ribs provided). If basket is replaced backwards cover will not fit on trap body. Clean and inspect lid Ring; reinstall on trap cover. Clean Ring groove on trap body and Replace lid. To help keep lid from sticking, tighten hand tight only. Prime pump (see priming instructions above)
READ MORE HERE: CONSTRUCTION POOL
PUMP SWIMMING POOL SB EMAUX
NGO GIA PHAT PRODUCTION TRADING CO.LTD Number 130, Cao Duc Lan street, An Phu ward, Distric 2, HCM city MST: 0312892690 Số tài khoản: 203474239, NH Á Châu – HCM Số tài khoản: 0531000282551, NH Vietcombank CN Q2 Tel: 0862 787 969 – 090 3366 556 – 0901 846 888 Email: [email protected] hoặc [email protected]
GOOGLE PLUS: BIOTECHPOOL